The DDTE034 OUTDOOR INTEGRATED TELECOM CABINET is mainly used in
wireless communication base station, such as 3G system,
communication/network integrated service, access/transmission
switching station, emergency communication/transmission, etc.
The cabinet, made of galvanized steel, is divided into equipment
compartments and battery compartments. The cabinet is easy for
installation, and with good sealing performance.
Equipment Compartment: The right part of the cabinet is equipment
compartment, which is separated from the battery compartment with
Battery Compartment: The battery compartment is used for installing
batteries. The cabinet body has heat insulation foam, which can
keep the temperature inside the cabinet. The cabinet includes
exhaust device, which can release harmful gas generated by the
Cabinet Door and Lock: The cabinet door uses embedded structure.
The door opening angle is larger than 110°and the door limit device
can limit the opening angle. The lock is theftproof three point
lock, supporting padlock. There’s open door alarm sensor, which
works together with the environment monitoring unit.
Cabinet Dimension: W×D×H 3200mm×800mmx2000mm
(1)The cabinet is dustproof, sunproof and rainproof, which is used
in outdoor environment.
(2)The equipment compartment and battery compartment cooling: fans
and air conditioner. (Other cooling option: heat exchanger).
(3)The layout of the cabinet is reasonable, which will facilitate
cable access, fixing and grounding. There’re entrance holes
individually for power cable, signal cable and optical cable.
(4)All the cables used in the cabinet are made from flame retardant
4. Technical Specs
(1) Applicable environment conditions:
Environment temperature: -40°C ~ + 60°C
Environment humidity (RH): ≤95% (at + 40°C)
Air pressure: 70kPa ~ 106kPa
(2)Material: hot dip galvanized steel
(3)Surface treatment: degreasing, derusting, rustproof phosphating
(or galvanizing), powder coated.
(4)Cabinet load bearing: ≥600kg
(5)Ingress Protection: IP55
(6)Flame retardance: comply with GB5169.7 test A
(7)Insulation resistance: the insulation resistance between
grounding devices and cabinet body parts is not lower than
(8)Withstand voltage: the withstand voltage between grounding
devices and cabinet body parts is not lower than 3000V(DC)/1min.
(9)Mechanical strength: each surface can bear upright
pressure＞980N; after the door is open, its outer end can bear
upright pressure ＞200N.